- Double flash high intensity
- NEMA 4X
- Meets UL1203 & UL1638
- Built in Synchronizable flash
- Xenon strobe lamp
- Available in amber, blue, clear, green, and red
- two year warranty on power supply
- one year warranty on lamp
Pendant Mount, 3/4” Hubs, Flange Mount, 3/4” Hubs, Wall Mount, 3/4” Hubs
|LED Lens Color||
Amber, Blue, Green, Red, Purple, Clear
|7120BEP–PMX||pendant mount, 3/4” hubs||120VAC|
|7120BEP–FMX||flange mount, 3/4” hubs||120VAC|
|7120BEP–WMX||wall mount, 3/4” hubs||120VAC|
Synchronizing Circuit Connection:
This is a low voltage, low power customer connection which requires one 22ga twisted pair run between each light. Max length between furthest lights 3000 feet. Up to 100 lights of different voltages can be synchronized.
Synchronizing Circuit Features:
Each light contains its own flash rate timing circuit which operates the lamp automatically and a bi-directional synchronizing circuit which overrides the internal timing circuit when connected to another light. When two or more lamps are synchronized together, failure of any lamp will not prevent other lamps from operating. Lights may be operated from different power sources, that is, a 120VAC unit may be synchronized with a 12VDC unit.
|Lamp Type||6001 Xenon strobe lamp|
|Flash Rate||80 flashes per minute|
|Light Output||890 candela eff.|
|Voltage and Amperage||120VAC 60 Hz draws 1.0A ( 1.7A max )|
|Power Supply Output||— AC and DC Units —
20 joules 1st flash
20 joules 2nd flash
|Operating Temperature||–40º C to +65º C|
|Temperature Code||T6 – All voltage and temperature ranges|
|Size and Weight||12” tall x 8.75” dia. x 13 lbs|
Visual signaling beacon shall be Tomar model number series 77120 or approved equal. The beacon shall be UL Listed Class I, Division 1, Groups C and D; Class II, Division 1, Groups E, F and G; and Class III for use in specified hazardous locations and /or combustible atmospheres as classified by the National Electric Code. The warning beacon shall have a 26 watt power supply and generate 20 joules per flash. Light intensity shall be 890 effective candlepower, and the light source shall be a plug-in field replaceable double-flash xenon strobe lamp operating at 80 flashes per minute. The warning signal must have built-in RFI filters to protect against radio interference and spike voltages. Beacon must have a built-in flash synchronizing circuit, and voltage range shall 120VAC. Strobe beacon must meet UL 1203, and UL 1638, standards. Beacon must be rated NEMA 4X, with housing made of die cast high-strength copper-free aluminum alloy with baked powder epoxy finish, stainless steel hardware, O-ring sealed pre-stressed globe with double pitch acme threads for smooth assembly and ease of maintenance. Must include a Lexan® inner lens and tempered glass outer dome. The housing must be designed to accommodate a dome guard.
Only logged in customers who have purchased this product may leave a review.